Complete overhaul of Washington Pump
Client informed us of problems related to their pump, including that of low flow rate, high vibration during operations and there as frequent bearing failures.
We were able to dismantle the whole pump unit in order to service every aspect of the pump contruction. These included a re-balancing, the restoration of the worn-out shalf, bearing replacements and using new packing seals. Finally, the pump screw (for both the male and female units) were also re-balanced.
The fully serviced Washington pump is now able to function again at its operational capacity to the satisfaction of our client.